window air conditioner - a candy bar, and so it is much easier to install than traditional split systems: You do not have to check the tightness of pipelines and lay freon route excluded high-altitude work, yessetting itself a specialist, if necessary, will be cheaper.
- Features and installation rules
- window air conditioner window air conditioner device
- Mounting kit for air conditioning
- Tools for mounting a window air conditioner installation
- household window air conditioner: sequence
- videos on youtube
features and rulesInstallation of window air conditioner
Installation involves mounting a window air conditioner in the window opening of equipment or too thick wall construction.The most common option to install a window air conditioner - is mounted in the process of replacing the window frame into the wall or partition, with the proviso that the wall thickness does not exceed 250 mm, the wall will otherwise prevent acc
Install window air conditioners household with their own hands - a very time-consuming work that requires a responsible approach, accuracy and precision performer, skills and professionalism: the master so the first thing is to compare the size of the air conditioner with the size of the window opening, and try to avoid distortions with respect to theirplane.Negligence necessarily result in damage to the air conditioner or the window frame, which will cause considerable additional costs.
normal, uninterrupted operation of the air conditioner is provided subject to the exact sequence of actions during the installation.It should focus on the following important point:
- Any air conditioning regardless of capacity and other technical parameters, envisages the laying of a separate wiring and the installation of "machine" in the control panel;
- not permissible gap between the planes of the opening for the installation of equipment and its case directly;
- Stained glass or plastic windows framed in aluminum or PVC impede installation of window air conditioner.
Basic rules of installation of window air conditioner:
- Air must be fixed firmly enough, otherwise his work will be accompanied by a loud noise.
- installed equipment should not be exposed to direct sunlight.
- outer side of a window air conditioner should protrude into the street at a distance of not less than 25-30 cm.
- Avoid using extension cords.Regardless of the location of the equipment, it assumes even require direct access to the accommodation zones of electricity.Install the air conditioner so that it was not far off.Using a home extension or perenosok strictly prohibited!If you need to lengthen the cable, use a special electrical extension cable, which is characterized by a lack of domestic electrical surges.
- outer panel conditioner should be located at a distance of 50 cm from the wall or other obstacles that would otherwise be difficult to normal air circulation and reduce the cooling capacity of the air conditioner.
- ventilation holes on the sides of the device, must not be an obstacle to access.
- order to reach the normal flow of condensate should be to install the air conditioner at a slight inclination of the outer side downward.The inside of the air conditioner should be 1-2 cm above the external.
- window air conditioner should be placed at a height of 75-100 cm from the floor.
- Do not forget about safety.Placement of the air conditioner in the window opening should not affect the safety of the premises.To secure the room in which is installed a window air conditioner, insert a small peg in a window profile so that it does not open from the outside.Otherwise, an attacker can effortlessly get into the house, barely parted the window and pushing a window air conditioner.
device window air conditioner
So, how to install window air conditioner?
To do this, the sequence of actions:
1. choose the place the air conditioner
to the installation of window air conditioner affects a lot of factors: for example, the geometry of space and the arrangement of furniture.To make the right decision should be guided by the following tips:
1. To begin with, visually inspect the window frame or wall surface - it will help to ensure their durability to install window air conditioner.Different in texture and strength of the materials and trim the outer and inner surfaces of the frame and the wall involve the use of different methods of fixing devices.Often used as fasteners anchor bolts, brackets and fastening corners sufficient strength.
If the inspection you come to a disappointing conclusion that the wall is not strong and eventually begin to break down the edge of the holes, then you will have to fortify the wall, because inaction in this case may fall and damage the window air conditioner, leakage or condensation and the appearance of strong noisevibration during operation.
If you are convinced of the strength of the wall, then go ahead and tighten the bolts and attach air conditioning.
edges of the window opening, or are already starting to crumble?You nothing left to do, how to strengthen the edges using a metal bracket.
If the wall on which is mounted equipment is not strong enough, it is necessary to expand the metal support, thereby reducing the load on the wall.
2. Carefully consider the mechanism of the condensate, which is formed by the continuous operation of the device.To water flowed smoothly, it is necessary to install air conditioners so that the rear part has been slightly (0.5-1 cm) is inclined downwards.At the same time must comply with strict balance between the right and left sides of the air conditioner, otherwise condensate can drain from the housing.
3. The air flow coming from the back of the air conditioner has a high temperature, so it should not fall on the plants, animals and humans.
4. Fixed air conditioner needs maintenance.For the convenience of that, experts advise to leave 10 cm of free space to the right or left of the device.For the normal circulation of cool air in the room it is recommended to place a window air conditioner in the middle.
5. Space and atmosphere around the air conditioner should not create obstacles to the continuous air circulation, otherwise it could face a sharp decline in its performance.
6. Fixed air conditioning Protect from direct sunlight by means of a pass from the sides and top of the equipment.This is important to the canopy does not prevent the normal circulation of air.
Mounting kit for air conditioning
Today you can choose various installation kits to install window air conditioners, for example:
Tools for mounting a window air conditioner
for quality installation of window air conditioner you need:
- cartridges for different drills (depending on the material, which will have to work - concrete, wood, metal);
- jigsaw Electric;
- handsaw for wood and metal;
- chisel to work with the window frames;
- Roller glass cutter (1 video at 10 meters);
- building level;
- Cut machine of the type "Bulgarians";
- seating area 2 types (internal and flat);
- silicone sealant opaque, white;
- latex paint and brush
Mounting household window air conditioner: sequence
Proper installation of window-type air conditioners with their hands holding involves the following steps and actions:
1. most time-consuming and difficult phase - thorough preparationunder the air conditioning of the window opening. Almost every window opening provides the optimum location for durable installation of the device.According to experts preferably carried installation in locations where the sides of the air conditioner (length and height), or at least one of them would be placed in the window opening with the smallest gap.To do this, the master will have:
- remove glazing;
- paste "bridge";
- cut glass according to the required size.
If you are in the role of an ideal place for a wall mount air conditioner choose, you must drill a small hole in the wall, mark the zone of fastening devices and its size.Then draw a line, as if to outline the future of equipment and drill holes using a drill at a distance of 5 cm from the similar lines.
a) when installing the air conditioner in the wall, its thickness shall be not more than 250 mm (one brick).Greater thickness can block the access of air to the air intake grille to cool the condenser, resulting in damage to the air conditioner.
b) when installing the air conditioner in the window opening distance between the frames should be between 250 mm and the window it must be equipped with windows.
2. Install the bracket and the housing window air conditioner
All models window air conditioners manufactured on the latest technologies, allow them to mount even regardless of whether the windows are opened or not, whether there is access to the outside or not.This happens thanks to a special device mechanism that can be withdrawn from the housing and attached to the wall or the bracket.CautionUnobstructed flow of condensate provides easy tilt-down rear of the unit.One should carefully check the seal and strength of the walls, otherwise the room can penetrate the wind and rain, and the fragility of the wall could lead to an increase in the load of arms on the floor surface.
Install window air conditioner into the prepared casing.
If at the time of transportation of the compressor or fan have been equipped with shock-absorbing pads, they should be removed before installation of the device, otherwise they will cause noise and vibration during operation.After installing the air conditioner into the case, make sure you have an angle of inclination of the back of the unit to ensure proper drainage.If you as a result of visual inspection found minor gaps and cracks between the housing, air conditioning and a wall, you should seal to prevent drafts.Often the air conditioner is equipped with a standard seal of the foam.Large cracks can be repaired with foam, while the small, barely noticeable - silicone sealant.If necessary, paint the damaged areas of the frame.
3. connect the drain hose
The work becomes a window air conditioner cooled the air, with the formation of moisture which in the absence of the drain hose will drain out through the drain holes conditioner, a process that is known to be undesirable.If you notice the bend or curve of the drain tube, then check for the absence of air pockets that prevent the outflow of water.It should be remembered: the tube must not touch the ground and the water in the tank.
4. Electrical power window-type air conditioner
window air conditioner operates in a voltage in the range of 90-110% of the nominal value.
Uninterrupted power conditioner may be carried out with the help of a separate line, equipped with a circuit breaker, which is also independent of the main fuse.
used during the installation of electrical equipment (wiring accessories, cables, wires for different purposes) must comply with quality and safety standards and the recommendations contained in the instructions for a particular model, the user's manual.
5. produce ground conditioner
performing work on earth, with extreme caution secure all terminals and wires.Invalid produced power equipment often leads to sudden failure.
6. to carry out work on the acceptance tests set by a window air conditioner
So, after installation, double check carefully the correct performance of all operations.Only after that the air conditioner is allowed to test its functionality and performance.All the problems found during the operation window air conditioner should be corrected in time.If you are unable to eliminate all the problems, you can use the services of specialists.
videos on youtube
with the installation of window air conditioner can be found by looking video.