Elektrodnye kotly Galan began the development of innovation in the technology of individual heating systems.Aggregates is a modern modification of the boiler with an electric central heating.In the classic model Galan TEN replaced the electrode assembly that decided the main problem of electric boilers - the fragility of operation of the heating element, made it possible to control the heating process of automatic modern systems.Saving energy in the electrode boilers is more than 30% compared to traditional electrical equipment.
- Benefits action electronic heating boiler Galan
- general principle of models Galan
- description of models of boilers Galan
- Installation boilers Galan
- boiler Galan.Wiring
Benefits action electronic heating boiler Galan
- Full thermal unit load progressively increases with increasing temperature of the coolant.
- reliable and economical heating system.
- Simple, balanced design of electronic components.
- use of modern automatic systems, the mobile parameter adjustment, support for the selected schedule.
- production of heat with the heated space, without exceeding or detracting energy delivered by a special built-in automatic system.
- Application of high-level automatic control is possible thanks to a controlled heating inertia.
- heat transfer medium entering the chamber of the boiler, warming from all their volume, which reduces the temperature rise and allows for a given parameter in minutes.Efficiency warming a cold room - the main advantage of boilers Galan.
- Soft start 50% of rated power.
- gated pipe system works better for heating radiators.
- use of modern materials for the manufacture of heating elements.
- Reliability at work "to failure."
- At the same power electronic boiler heats the coolant flow is 1.5 times faster than electric.
- ability to automatically maintain a minimum temperature in the prolonged absence of people in the home.This factor reduces power consumption up to 50%.
- do not emit carcinogenic gas or smelly exhaust.The level of environmental performance evaluated on Euro III.
general principle of models Galan
- principle is based on the laws of physics and chemistry, as well as the law of the transformation of one energy to another.
- Under the influence of the electrode in the liquid is the splitting of the negative and positive ions.
- There is a natural motion of the charged particles begin to connect oppositely charged into one, while stressing the large amount of energy.
- In this process begins heating the coolant.
- described process takes place without the participation of a third element, such TENa.
- Rapid heating of coolant leads to increased pressure in the boiler up to two atmospheres.
- Water under pressure is pushed out into your heating system.An analogue of - natural geysers, coffee makers, etc.
- Created water pressure of water more than 25 meters, the system provides a full circulation of coolant around the perimeter of the pipe.
description of models of boilers Galan
1. Model Galan-03 center:
- The compact design of the unit is considered to be the smallest of all known analogues.
- unique lightweight aggregate 500 g in combination with a power output of 5000 watts allows heat the room volume of 250 m3.
- Filling and productive operation of the system is sufficient 70 liters of water.
- peculiarity start unit is a low energy threshold, maximum is reached after 12 A.
- further warming of the system leads to an increase in resistivity, increase power to a nominal figure.
2. Model Galan Geyser:
- sets of medium size and power.The most popular consumer model.
- compact design combined with high power of 9000 W allows you to use the model for heating private houses with a total area of 200 m2.
- feature is the ability to connect the boiler Galan, a geyser to a one- or three-phase power systems.
- for filling the heating system you need 300 liters of water, which is slightly larger than the volume of water for a standard bath.
- Net unit 7 kg makes it possible to install miniboiler in a small room, disguise it in the interior.
3. Model-Galan Volcano:
- miniboiler most powerful brand in the lineup.
- Power unit 25000 W offers advantages in the use of systems for medium-sized private farms in several houses, for use heating private pensions, small production facilities with a volume of 800 m3.
- power source for connection - single-phase or three-phase.
- volume of water filling of 500 liters.
- maximum generated pressure to 2 atmospheres.
- Net unit 7 kg.Possibility to install in a limited space in the narrow business premises.
Installation boilers Galan
1. Features of the boiler Galan:
- compact design, low weight unit Galan create optimal conditions for easier installation.
- savings during installation of the electrode boiler Galan.No need to install the boiler, pump and other accessories, like the classical heating electric boilers.
- Use as a heat transfer fluid purified, distilled water.The liquid is not discharged from the heating system in winter, do not freeze at - 40 C.
- Indispensable for thermal insulation of walls treatment and protection from heat.
2. Necessary safety precautions:
- When installing the electrode boiler system performed compulsory grounding of the unit.
- All terminals and current-carrying parts of the unit protected from moisture and contact with the surface of the boiler.
- Set breaker - switch for current cutoff.Recommended Machine 25 A.
- Follow connection schematic plan recommended in the data sheet for specific model Galan.
- Mandatory requirement - to observe the connection faza - nol - zemlya.
- Before starting the boiler check the tightness and rezbovyh svarnyh soedineny.
- exclude the possibility for water at popadaniya Open body parts and ion kotla.
- to management and electronic ekspluatatsii kotlami Galan dopuskayutsya people over 18 years old, familiar with TB who have experience with afterwards the installation of this type.
- mandatory requirement in normal operation - nalichie rasshiritelnogo baka.When
- education sisteme The heating ice disable kotel From sistemy and conduct defrosting.
3. Preparatory phase:
- Mounting of The heating sistemy.When assembly is the main condition - the observance chistoty truboprovoda, excluding penetration polost metallicheskoy ctruzhki, postoronnih substances.
- Compulsory Rough # Cleaning of the filter is connected.
- By okonchanii Mounting of cistem tschatelno washed ingibitorom Galan.
4. Installation of boiler Galan:
- The boiler system is made in a vertical position, with the arrangement of the protective cap at the bottom.
- Use cast-iron radiators.The electrolysis process causes iron to a state not condition.In the electrolysis, chemical constituents lattice iron ions react chemically with ions coolant.As a result, formed in the metal shell begins progressive corrosion.Modern ferro alloys have a high resistance to electrolytic solutions.
- boiler necessarily attached to one wall of the room.The method of connection to the heating system is not critical.
- Valves not installed between the outlet and the expansion tank.
- by professional grounding of the heating system.Select the wire with a cross section of 2.5 m, which provides resistance index of 0.1 Ohm.
- boiler connection to the mains is carried out only by specialists - electricians, having a certificate of admission to work on the electrical system up to 1 kW.
- All work performed on electrical neobluzhennymi stranded copper conductors.Wire size is selected for the respective current loads.
- end of the wire to connect carefully stripped from the oxide film and insulating material.
Apply several circuits connecting the unit Galan:
1. Schematic diagram.Available in the following order:
- Miniteplovaya station Galan.
- radiator heating unit with shut-off valve.
- temperature switch sensor and display readings.
- expansion tank.
- valve to drain.
- shutoff valve.
- circulation pump with a filter element.
2. Parallel connection.Produced with the following arrangement:
- Liquid or solid-gas unit.
- heating radiator unit with shut-off valve.
- relay temperature control sensor.
- expansion tank.
- valve to drain.
- shutoff valve.
- circulation pump.
- selected model boiler Galan.
3. SUGGESTED wiring:
- -breaker of 25 A.
- magnetic starter 25 A.
- Temperature sensors in / out.
- reel magnetic starter.
- Relay heat.
- LED power / ammeter.
- boiler Galan.
4. Rule of sensor:
connection electrode boiler Galan made by the scheme described.Be sure to observe the correct location of the sensors:
- incoming temperature sensor.It is installed on the outlet pipe of the last section of the radiator.
- sensor for outgoing temperature parameter is always set on coming out of the boiler piping.
- Joining both sensors are stranded copper wire.Wire size from 0.5 to 1 mm2.
- Automatic 25A required for overload protection in the power supply is used as a conventional on / off switch.
- normal, working position of the button to disable / enable the thermal relay - Recessed.The button is located on the body of the magnetic starter.Button operation indicates a fault in the mains.After a fault, the inclusion of the thermal relay by pressing the button.
5. Installing the operating parameter of the temperature:
- Output flow temperature is adjustable between 70-75 C.
- inlet temperature is calculated based on many factors: the volume of the heating system, the temperature of the surrounding atmosphere or the air space inside the building,the amount of space being heated, and the index of the state of thermal insulation protection facilities.The recommended value of the incoming flow of 40 to 45 C.
- switch on circuit breaker.Proper connection will lead to rapid heating of the heating system, as witness the ammeter.Display of current parameter will not be less than 23 A.
- Using the boiler in normal mode automatically.Reaching the limit temperature parameter will disable the boiler Galan.Lowering the temperature of the coolant - to trigger automatic activation.
- sensor detects input parameter set the temperature in the radiator sections.The increased boiler shutdown triggers.Lowering the setting provokes its inclusion.
6. Selection of coolant models Galan:
- Selection of liquid coolant electrode boilers produced with great care.From the composition and quality of water depends on the age and productivity of the machine.
- necessary to match the water quality of drinking water.
- Alternatively use boiled water with the addition of an inhibitor Galan.
- resistivity of the coolant at + 15 C is not less than 1300 ohm / cm. The measurement indicator is a special device - conductivity meter.
- best coolant - a special fluid designed for use in boilers Galan.